Table of Contents
System Abnormal Fire Alarm System Minerva T1016 ASL Scorpio
- Equipment Fire Alarm System
- Fire Alarm Control Panel
- Fire Alarm Sensor Smoke and Heat Detector
- Brand Tyco
- Type 601P-M Conventional
- Product By Tyco Safety Product, UK
- Condition General Fault.
- Some detector is not functioning.
- Some Break Glass is not function.
- Zone consists of:
- Zone Location / Area
- Zone 1 Navigasi Bridge Deck
- Zone 2 Bridge Deck
- Zone 3 Forecastle Deck
- Zone 4 Main Deck
- Zone 5 Engine Room
- Zone 6 Bow Thruster Room
- Zone 7 Steering Gear Room
- Zone 8 Emergency Genset Room
Repairs on the control unit:
|9 Volt battery replacement. This battery is a battery backup to save all the settings and system configuration|
|9 Volt battery replacement. This battery is a battery backup to save all the settings and system configuration 2|
|Replacement of two microswitch, namely: accept and reset switches.|
|Installation / additional resistors on all unused output control. Because the resistor as the end of the line representing the zone system. Avoid general fault indication.|
1. Checking the performance of all of the detector.
2. One detector was found broken, need replacement.
|One detector was found broken, need replacement.|
1. Checking the performance of all of the brake glass.
2. Two unit Break Glass was found broken, need replacement.
|Two unit Break Glass was found broken, need replacement.|
- The system has worked normally.
- General fault does not appear on the screen.
- It has been done with smoke test smoke testing.
|Fire Alarm Control Panel Unit|
|Screen On Fire Alarm Control Panel|