Check and Service Sewage Submersible Pump Ocean Clean Panel ASL Scorpio
Equipment Sewage Submersible Pump
- Brand Ocean Clean
- Type 0,5 EB
- Serial 609239
- Built 03, 2007
- Capacity 0,5KW
- Power Voltage 440 VAC
- Control Panel does not work, some cables regardless of the terminal.
- Some components of the panel is not in place / missing.
- Some buttons and indicator lamp broken.
- Re-install the panel, in accordance with existing drawing,
- Replace some damaged panel components, including: fuse and terminal,
- Replace broken buttons and indicator lamp.
- The panel has been working fine, after reinstallation,
- Motor sewage has been tried and running normally,
- Changes made to: Not using automated methods, this demand CE, by reason of the hole where the height sensor placement has been closed and is no longer possible to use.
|Sewage Submersible Pump Panel Unit
|Contactor for Motor Sewage Pump